Our Raychem RSTI-VS Separable Connectors with Voltage Sensor 630A/1250A are bushings C type which integrates voltage measurement and Partial Discharge monitoring and detection functionalities in transformers and switchgear up to 24 kV.
Our Raychem RSTI Separable Connectors with Voltage Sensor are designed to increase network transparency and support the implementation of smart grids.
Our Raychem RSTI Separable Connectors with Voltage Sensor is the new generation of screened separable connectors. The separable connector with voltage sensor fits 630/1250A bushings type C as specified by EN 50180 and EN 50181 and is suitable for both new and retrofit installations up to 24 kV.
In conjunction with the new generation of Intelligent Electronic Devices (IEDs), the voltage sensor provides a measuring signal for grid management applications like monitoring, power quality, protection or metering, as well as asset management applications, like PD monitoring.
The capacitive voltage divider concept is used in the voltage sensor technology for passive medium voltage instrument transformers.
This concept provides intrinsic safety and protection advantages for the operation of sensors in power networks due to the galvanic isolation from high voltage. It also provides an appropriate signal for on-site partial discharge monitoring.
In addition, the compact design provides complete integration within the smart separable connector, as well as full encapsulation through a grounded and conductive outer screen.
Very compact design to fit easily in compact switchgears
High accuracy over a wide temperature range
High accuracy on higher harmonics for reliable power quality applications
Type-tested according to both IEC 61869-11 and CENELEC HD 629.1 S2
Inherent safety thanks to total galvanic isolation from high voltage
Simple connection as no auxiliary power supply is needed due to passive components
Factory-calibrated thus no need for on-site calibration
Question: How can I precisely measure voltage/current in distribution networks?
Answer: To precisely measure the voltage or current in your power distribution network, you can use our Raychem Separable Connectors with Voltage Sensor. They will help you to improve the transparency of your network and to implement a smart grid.
Question: Can I use voltage sensors in secondary substations?
Answer: Yes, our Separable Connectors with Voltage Sensor can be installed in secondary substations. They are suitable for both new and retrofit applications.
Question: What are “smart cable accessories”?
Answer: Smart cable accessories, such as our Separable Connectors with Voltage Sensor are devices that enable signal measurement for grid management such as monitoring, power quality, protection, or metering.
Question: What is the reference standard for voltage sensors?
Answer: The reference standard for voltage sensors is IEC 61869-11 for a low power instrument transformer.
Question: How are the Separable Connectors and Voltage Sensors tested?
Answer: Our Raychem Separable Connectors and Voltage Sensors are tested according to cable accessories standard HD 629.1 and low power instrument transformer IEC 61869. Their compliance with these standards ensures a long-lasting and reliable performance of our products.
Please carefully read the disclaimer before using any of this data. Your use of this data constitutes your acceptance of the terms and conditions set forth below. If you do not agree to those terms and conditions, please click on the I Disagree link.
This information has been provided to your free of charge for your use but remains the sole property of TE Connectivity Corporation (''TE'') or SnapEDA, Inc. or Ultra Librarian/EMA Design Automation, Inc. (collectively, "Company"). While Company has used reasonable efforts to ensure its accuracy, Company does not guarantee that it is error-free, not makes any other representation, warranty, or guarantee that the information is completely accurate or up-to-date. In many cases, the CAD data has been simplified to remove proprietary detail while maintaining critical interface geometric detail for use by customers. Company expressly disclaims all implied warranties regarding this information, including but not limited to any implied warranties or merchantability or fitness for a particular purpose.