The high voltage outdoor termination (OHVT) is designed to operate under severe environmental conditions. Polymeric insulated cables of various designs can be adopted with respect
to shielding and metal sheath. Composite or porcelain housings with different creepage lengths are available covering the most common and also extreme pollution levels. The installation of the termination can be
done by trained installer equipped with conventional tools. The termination is designed according to the following standards:
IEC-60840, IEC-62067, IEC-60815, IEEE-48, IEEE-1313.
The cable lug is suitable for all common conductors made of aluminum or copper. The flexible double sealing system is installer-friendly and ensures permanent protection against environmental influences of the top
assembly. A heat-shrinkable polymeric tube containing oil-resistant sealant encapsulates the connector barrel and the polymeric insulation transition. The pressure-tight composite housing is made of a glass fiber reinforced
(GFR) resin tube with silicone rubber sheds molded to the tube. The interface between stress cone, cable insulation and inner housing will be filled from the top with silicone oil. No prior heating of silicone oil required.